ProtoCessors are a family of low-cost TTL to RS-485, Ethernet, and LonWorks embedded coprocessor modules that enable original equipment manufacturers (OEM) to connect to the cloud and rapidly implement various industrial, building, and machine automation protocols in their products.
The ProtoCessor provides OEMs the ability to fully configure the OEM IIoT gateway module to meet specific product, customer, or application needs, yet still utilize the same socket and hardware of an OEM electronics board. The manufacturer downloads the new configuration via a downloadable file or host PC.
The ProtoCessor is BTL (BACnet Testing Laboratories) Marked, LonMark Certified, DNP3 Conformance Tested, and RoHS Compliant. These approvals and certifications assure our customers that we carry only the highest quality of products and performance.
This product is protected by FieldSafe.
1. SMC Device Cloud support
Register your ProtoCessor to the SMC Cloud interface for remote access to local applications, configuration, and device management
2. Rapid Time-to-Market
Minimize coding and hardware demands or changes to current OEM design
3. Reduced NRE (Non-Recurring Expenses)
Reduce costs on purchases of source code and engineering time
4. TTL Form Factor
Fits on any OEM’s PCB circuit board hardware for maximum flexibility and ease-of-installation
5. Serial, Ethernet, or LonWorks Environment Support
Provide multiple protocol support for any protocol translation as a full-featured, field-programmable OEM protocol gateway solution
6. Multi-Client Support
Ensure interoperability between any industrial and/or building automation protocols
7. BACnet COV (Change of Value)
Provide fast data communication while reducing traffic over a BACnet network
8. BACnet COV (Change of Value)
Automatically discover known devices on the network and be configured to provide the protocol translation necessary
9. Configuration Auto-Selector
Enable manufacturers to pre-load multiple predefined configuration
10. Proxy Tunnel
An SMC Cloud feature that allows users to view the web page on their remote device via the remote FieldServer
This FieldServer feature assists users enter valuable site information to enable rich analytics when analyzing or diagnosing data from all sites via the SMC Cloud
12. Virtual Data Points
A rich Edge Gateway feature that enables manipulation of device data on the FieldServer to produce useful data using a JSON logic engine embedded in the FieldServer Gateway
FFP-ETH: Ethernet RJ-45 (8-pin)
FFP-485: RS-485 3 way Phoenix connector
Standard Serial TTL Interface-TX and RX
Socket on Board: 2 x 10 20-pin
Ambient: -40o to 185oF (-40o to 85oC)
Storage: -40o to 257oF (-40o to 125oC)
Humidity: 5 to 90% RH
FFP-ETH: 5 VDC @ 208 mA
FFP-485: 5 VDC @ 350 mA
FFP-LON: 5 VDC @ 480 mA
FFP-ETH: 1.8 x 1.2 x 0.8 in. (4.6 x 3.0 x 2.0 cm)
FFP-485: 2.7 x 1.2 x 0.8 in. (6.9 x 3.0 x 2.0 cm)
FFP-LON: 3.3 x 1.2 x 0.8 in. (8.5 x 3.0 x 2.0 cm)
|Settings on FFP-485||
DIP switches set Baud Rate, MAC address, Device Instance, selection of stored predefined configuration files, and end of line termination for RS-485 networks.
|LonMark Certificatoin on
SPID: 80:00:95:46:00:84:04:05 Profiles:
Various ProtoCessors have the following third party approvals:
Please contact the OEM vendor of your ProtoCessor to ask for the Start-up guide for the specific ProtoCessor. The output protocol can be configured a number of different ways on the ProtoCessor and the OEM Vendor will have the correct documentation on how to set it.
The ProtoCessor mapping has been pre-configured and approved by the OEM Vendor. MSA Technical Support is not authorized to change it. Please contact your OEM Vendor to inquire about any modifications to the mapping.
Please contact the OEM vendor of your ProtoCessor to ask for the Start-up guide for the specific ProtoCessor. There are several ways of changing the Device Instance on a ProtoCessor Gateway and the OEM Vendor will have the correct process documented in their Start-Up guides.
Recovery Mode occurs when an internal Module of the ProtoNodeCessor firmware has suffered a crash or corruption. A firmware upgrade will be required to resolve.
i. Take a Diagnostic Capture and Contact Technical Support
- Download and install the FieldServer Toolbox.
- Connect to the ProtoCessor’s Ethernet port
- Hit the Diagnostic button on the FieldServer Toolbox
- Take a 5-minute, Full Diagnostic of the ProtoCessor
- Email the zip file to email@example.com. Be sure to include your observations and what you would like Technical Support to check